Regular Post - Small - $0.00 Regular satchel: Australia Wide via Australia Post including to PO Boxes & Post Offices. $100 shipping insurance included, if more insurance is required please contact us.Australia Post Express Satchel - Small - $11.90 Express satchel: Australia Wide via Australia Post including to PO Boxes & Post Offices. $100 shipping insurance included, if more insurance is required please contact us.Pick Up From Rowville Warehouse - $0.00 Pick up from Solar 4 RVs Rowville warehouse within normal business hours. Please allow 24 hours before collecting order. For urgent pick up, please call or email.
This document is the manual for the 3 phase max 65A per phase Energy Meter.
The Energy Meter can be used to:
Grid meter, and used as control input for an ESS System (1).
Measure the output of a PV Inverter
Measure the output of a AC Genset
The meter is connected to the Color Control GX. There are two options in its wiring:
Direct connection, either using the RS485 to USB interface with 1.8m cable length, or the 5.0m cable.
Wireless connection via Zigbee
When used to measure a PV Inverter, terminals 1, 2 and 3 should face the PV inverter to ensure correct direction of current and power.
Single phase dual function diagram:
In this diagram, a single meter is used to both measure the grid and a single phase PV Inverter
On the CCGX go to the grid meter in the Wired AC sensor settings. Make sure 'Phase type' is set to 'Single phase' and 'PV inverter on phase 2' is enabled.
Wired connection to CCGX
Connect the Energy Meter to the CCGX using the USB to RS485 cable. The RS485 to USB interface cable between the CCGX and the Energy Meter can be extended up to 100 meters; make sure that the extensions of the Data+ (orange) and Data- (yellow) wires form a twisted pair.
The red, green and brown wire coming out of the USB to RS485 cable are not used.